Shanghai Metal Corporation is a leading Polyethylene Water Supply Pipe manufacturer and supplier.
PE pipe is a non-polar thermoplastic resin with high crystallinity. The inner wall of the PE water supply pipe is smooth and does not change with the use of time. The friction resistance is small, saving energy. The pressure loss is about 30% smaller than that of the steel pipe. A smaller caliber can be selected than the steel pipe. ISO standard grade polyethylene material is grade 0 (lower grade), no mold material, compared with some other commonly used plastic materials, polyethylene's mold resistance It is much higher and does not accumulate in long-term use.
If you want to know more about our Polyethylene Water Supply Pipe or get Pipe price please feel free to contact us, we will reply you within 24 hours.
a. The inner wall is smooth, and the flow resistance is small, so the construction cost is saved.
b. Has good weather resistance (including UV resistance) and long-term thermal stability.
c. It can be used safely in the temperature range of -20--40℃, and construction in winter is no problem.
d. Polyethylene raw materials contain only two elements, carbon and hydrogen, which are harmless to human body.
PE water supply pipe can be used for general purpose pressure water delivery and drinking water delivery.
Mainly include municipal buried water supply, building water supply (drainage), farmland irrigation, waterscape engineering, etc. In the water supply pipeline project, the PE water supply pipe will eventually replace the UPVC pipe.
Packing of PE Water Supply Pipe:
PE pipe welding method:
1. Preparation for PE pipe welding: Check whether the power supply of the hot melt machine is connected, whether the milling cutter and heating plate are ready, and whether the rack cylinder is running.
-Remove the dirt (oil, dust, mud, water) from the pipe port.
- Place the PE pipe in the rack slip.
- Mill the end face of the PE pipe with a milling cutter.
- Measure the power of the frame cylinder support.
-Check whether the temperature of the heating plate reaches the temperature value between 190-230, 210±10℃ at normal temperature.
-Put the heating plate into the rack.
-Reduce the welding pressure (0.02Mp).
-Switch quickly after the time is up.
-Increase the pressure to meet certain requirements, generally 2-3Mp, depending on the power of the cylinder support.